Occasionally it is necessary for employees of Reedsburg Utility to work on electric meters and transformers located near or on your property for routine maintenance and testing. These activities are needed to accurately measure consumption and assure a reliable source of electrical energy.
Access to that equipment is critical for the safe and efficient performance of these very important tasks. Because of this needed access and the safety issues involved, there are certain regulations and guidelines that are outlined in the National Electric Code and The Wisconsin Administrative Code.
Some of these rules are:
There shall be a minimum of three feet of unobstructed working space measured from the meter face in front of the meter. This space shall extend from the floor or ground level to a height of six feet three inches.
The unobstructed space in front of meter cabinets, current transformer cabinets and transformer loss cabinets shall also be from grade to a height of six feet three inches. This requirement is defined in the National Electric Code Section 110-16.
Underground transformers require eight feet of workspace to the front of the transformer, three feet on the sides and two feet in the back.
For underground pedestals, the available workspace must be three feet on all four sides. It may be necessary for Reedsburg Utility personnel to get near equipment if shrubs are planted too close or other materials are stored too near, you may be asked to remove the obstructions. Please understand that these rules and regulations are in force to help Reedsburg Utility maintain the electrical equipment that provide you low cost reliable electrical energy and to ensure the safety and efficiency of our employees.
Your cooperation is greatly appreciated. If you have questions about this or other energy concerns, contact us at 524-4381.